The ECL Comfort electronic heating controller is matched with a full range of ECL Application Keys. Each Application Key is programmed with specific parameters for a particular district heating or cooling application.
The ingenious ECL Application Key makes it easier than ever to install and set up your heating system application in the ECL controller – all without any need for advanced programming.
The data programmed in every ECL Application Key incorporates dedicated and applied expertise from worldwide experience with various applications. This is your best guarantee for optimum system performance.
The many different application keys for the electronic controllers ECL Comfort 210 and 310 makes it easy and fast to control your heating system and obtain energy savings due to higher efficiency. The "A2xx" application keys can be used both with the ECL 210 and 310 controller. The "A3xx" application keys can only be used with the ECL 310 controller.
Features and benefits
Many different application keys
Programmed data incorporates applied expertise from worldwide experience
Easier installation and set-up of the heating system application in the ECL controller
District heating application guide
We share experience, application expertise and make recommendations on optimum performing DH applications and key applied control components
A368 appl.-key was originally made with A368.1, A368.2, A368.3 and A368.4.
As per January 2014 the A368 appl.-key contains two extra subtypes, A368.5 and A368.6.
Main items in A368.5:
F1 is a flow meter to measure the refill water volume. The pulses from the flow meter are applied to the ECA 32 module's pulse input.
S11 is temp. monitoring of heating, secondary return.
S13 is temp. monitoring of DHW circulation, return.
Main items in A368.6:
S2 is temp. monitoring of heating, secondary return.
S8 is temp. monitoring of DHW circulation, return.
One DHW circulation pump (P1).
Mounting Guide has been updated.
Installation Guide in English has been updated.
A247 was originally made with A247.1, A247.2, A347.1 and A347.2.
As per January 2014 the A247 appl.-key contains an extra subtype, A247.3.
Main differences, compared to A247.1:
S7 is DHW-charging temp. Sensor
S4 is DHW-heating temp. Sensor
P2 is DHW primary circuit circulation pump
P4 is DHW-charging pump.
Mounting Guide has been updated.
Installation Guide has not been updated yet.
Solar heating plant reduces CO2 emissions by 15,700 tonnes annually
The world’s largest solar heating plant in Silkeborg, Denmark harnesses energy to heat the homes and workplaces of 40,000 citizens. It supplies 18-20% of the annual heat consumption in the city of Silkeborg, Denmark, which has an ambitious target of CO2 neutrality in heat production by the year 2030.
Heating facility reconstruction in Kopaonik mountain resort, Serbia
Application: Hydronic balance, control and monitoring of a heating system
Challenge: Improve the energy efficiency of old heating system
Solution: Danfoss installed motorized control valves, hydronic balancing valves and electronic controllers with monitoring software
District energy as the heating and cooling solution in Teknopark Istanbul, Turkey
Application: Production of heating, cooling and domestic hot water
Challenge: Design and construct customized district energy solutions for all buildings on the park
Solution: Danfoss designed and constructed 3 pre-assembled DSE substations containing control valves for the heating, cooling and domestic hot water, heat meters, self-acting controllers and electronic controllers connected to a central Building Management System.
Renovation of a district heating network, Tuzla, Bosnia and Herzegovina
Since 2011, the local District Heating Company (“Centralno grijanje” d.d. Tuzla) has carried out a major renovation of the city’s comprehensive district heating network, providing reliability of supplies, improved comfort as well as energy and cost savings. Based on thorough analysis and a long-term strategic approach, the 30 year old system is gradually transformed into a modern and smart energy system.
First ever district heating system with substations in Turkey
600 residents in the town of Soma in Western Turkey now enjoy the comforts of a reliable and cheap heat supply from the town’s brand new district heating system.
In the coming years, more than 8,000 households will be joining the system that exploits the excess heat from the municipal power plant – a great improvement from the charcoal boilers of the past, and much less expensive.
District heating network in HafenCity, Hamburg, Germany
The district heating supply in the new Hamburg city quarter "HafenCity" is a costeffective and sustainable solution amongst other supplied by Danfoss.