The ECL Comfort electronic heating controller is matched with a full range of ECL Application Keys. Each Application Key is programmed with specific parameters for a particular district heating or cooling application.
The ingenious ECL Application Key makes it easier than ever to install and set up your heating system application in the ECL controller – all without any need for advanced programming.
The data programmed in every ECL Application Key incorporates dedicated and applied expertise from worldwide experience with various applications. This is your best guarantee for optimum system performance.
The many different application keys for the electronic controllers ECL Comfort 210 and 310 makes it easy and fast to control your heating system and obtain energy savings due to higher efficiency. The "A2xx" application keys can be used both with the ECL 210 and 310 controller. The "A3xx" application keys can only be used with the ECL 310 controller.
Features and benefits
Many different application keys
Programmed data incorporates applied expertise from worldwide experience
Easier installation and set-up of the heating system application in the ECL controller
A368 appl.-key was originally made with A368.1, A368.2, A368.3 and A368.4.
As per January 2014 the A368 appl.-key contains two extra subtypes, A368.5 and A368.6.
Main items in A368.5:
F1 is a flow meter to measure the refill water volume. The pulses from the flow meter are applied to the ECA 32 module's pulse input.
S11 is temp. monitoring of heating, secondary return.
S13 is temp. monitoring of DHW circulation, return.
Main items in A368.6:
S2 is temp. monitoring of heating, secondary return.
S8 is temp. monitoring of DHW circulation, return.
One DHW circulation pump (P1).
Mounting Guide has been updated.
Installation Guide in English has been updated.
A247 was originally made with A247.1, A247.2, A347.1 and A347.2.
As per January 2014 the A247 appl.-key contains an extra subtype, A247.3.
Main differences, compared to A247.1:
S7 is DHW-charging temp. Sensor
S4 is DHW-heating temp. Sensor
P2 is DHW primary circuit circulation pump
P4 is DHW-charging pump.
Mounting Guide has been updated.
Installation Guide has not been updated yet.
Tools and apps
District heating application guide
We share experience, application expertise and make recommendations on optimum performing DH applications and key applied control components
Intelligent optimisation of district energy in new residential apartmentsTwo new build apartments in Docklands, London and Newbury Racecourse, Berkshire have been equipped with intelligent Danfoss solutions, bringing increased control and stability as well as greater than 20% peak energy reduction.
Solar heating plant reduces CO2 emissions by 15,700 tonnes annuallyThe world’s largest solar heating plant in Silkeborg, Denmark harnesses energy to heat the homes and workplaces of 40,000 citizens. It supplies 18-20% of the annual heat consumption in the city of Silkeborg, Denmark, which has an ambitious target of CO2 neutrality in heat production by the year 2030.
District energy as the heating and cooling solution in Teknopark Istanbul, TurkeyBuilding: Office Application: Production of heating, cooling and domestic hot water Challenge: Design and construct customized district energy solutions for all buildings on the park Solution: Danfoss designed and constructed 3 pre-assembled DSE substations containing control valves for the heating, cooling and domestic hot water, heat meters, self-acting controllers and electronic controllers connected to a central Building Management System.
Heating facility reconstruction in Kopaonik mountain resort, SerbiaBuilding: Hotel Application: Hydronic balance, control and monitoring of a heating system Challenge: Improve the energy efficiency of old heating system Solution: Danfoss installed motorized control valves, hydronic balancing valves and electronic controllers with monitoring software