Pressure and differential pressure relief controllers consist of a valve and a pressure actuator. Primarily used to limit a pressure (A) or differential pressure (PA)
over a system/substation/pump.
Controllers are normally closed: AV(P)A due to a normally closed valve and AF(P)A due to a stretching spring.
Pressure and differential pressure relief controllers are primarily installed into a bypass. They can be used to enable heat power distribution to other network connections or idle flow in case the connection(s) close(s) completely.
Pressure and differential pressure relief controllers can protect variable flow pumps from overload in the event that flow falls below minimum pump capacity. They relieve pump/application and forward heat power to other connections.
A pressure relief controller can also be installed into the return to maintain a higher desired (static) pressure in the system.
Features and benefits
Relief pump/application and forward heat power to other connections safely
Made for demanding systems, resistant to corrosion, cavitation and dirt
Connected system is protected against pressure surges, fluctuations, cavitation and noise
Differential pressure and flow controllers in district heating or cooling systems (variable flow)
Balance your network, save energy and improve end user comfort by hydronic balancing and control of district energy networks.
Tools and apps
District heating application guide
We share experience, application expertise and make recommendations on optimum performing DH applications and key applied control components
Yes you can. Open the control valve fully and set the max flow by adjusting the differential pressure. You can also calculate the appropriate differential pressure, but you need to know the exact capacity of the control valve.
We produce valves with a standard length. You can also find the measures in our datasheet or download 2D and 3D CAD drawing models from our product presentations. Please go to our product catalog where you will find links to documentation and drawings - follow the below link.
Do not stop turning the setting nut when the shaft hides into it. There is still round 100 mm stroke to do.
Solar heating plant reduces CO2 emissions by 15,700 tonnes annuallyThe world’s largest solar heating plant in Silkeborg, Denmark harnesses energy to heat the homes and workplaces of 40,000 citizens. It supplies 18-20% of the annual heat consumption in the city of Silkeborg, Denmark, which has an ambitious target of CO2 neutrality in heat production by the year 2030.
District energy as the heating and cooling solution in Teknopark Istanbul, TurkeyBuilding: Office Application: Production of heating, cooling and domestic hot water Challenge: Design and construct customized district energy solutions for all buildings on the park Solution: Danfoss designed and constructed 3 pre-assembled DSE substations containing control valves for the heating, cooling and domestic hot water, heat meters, self-acting controllers and electronic controllers connected to a central Building Management System.
First ever district heating system with substations in Turkey600 residents in the town of Soma in Western Turkey now enjoy the comforts of a reliable and cheap heat supply from the town’s brand new district heating system. In the coming years, more than 8,000 households will be joining the system that exploits the excess heat from the municipal power plant – a great improvement from the charcoal boilers of the past, and much less expensive.